Module/Rack AIC Ratings
A.I.C. is an acronym for "Ampere Interrupt Current". It has been replaced recently by the term "RMS Symmetrical Current". The AIC rating is the maximum current that can flow through a piece of equipment without permanent damage. If a direct short is applied between the phase bars of a rack, this allows the current protection to trip before damage occurs.
At ETC, we typically use this term when referring to dimming racks. Here are the guidelines:
Sensor SR/SRN Series Racks
The dimmer module in the rack with the lowest AIC rating determines the AIC rating for the entire dimming rack.For Unison DR Series Racks
The racks have the following AIC ratings:
You apply the DR rack rating first and then, the dimmer module in the rack with the lowest AIC rating determines the AIC rating for the entire dimming rack. (A D20 with an AIC of 100,000 in a DR6 would give you a total AIC for the installation of 10,000) AIC ratings for Dimmer Modules
Share the ETC love! Do you think this information would be helpful to a friend? Fill out the form below to send the page to other recipients, or send it to yourself to save for future use.