There is a topology issue to consider with SmartLink interconnected S-ACPs that can result in erratic system response to SmartLink commands. This issue only affects systems with two or more S-ACPs on the SmartLink bus. A single S-ACP connected via SmartLink to SmartPack, SmartSwitch, or CEM+ with SmartLink Power Supply functions normally.
When connecting multiple DRds with S-ACPs together using SmartLink (e.g. Belden 8471 or approved alternate), you need to adjust the termination jumpers in the secondary racks. The DRd that houses the S-SPM should use the default HALF Lon Termination, and its S-ACP should be configured as station master. The other DRds should not be configured as station masters, and their Lon Termination should be set to Off.
Share the ETC love! Do you think this information would be helpful to a friend? Fill out the form below to send the page to other recipients, or send it to yourself to save for future use.