The attached document provides guidelines for the different wire types, and their equivalents, that ETC recommends for low voltage data transmission in permanently installed lighting systems.
When equipment goes bad out in the field, it's often extremely helpful if the owner/end user can keep track of the circumstances of the failure. This is especially true when the problem is intermittent and might not occur when the technician is present. Service Technicians are exceptionally skillful...
ETC Product Wiki
Filed under: AAS, Acclaim, arri, ASTS, AVAB, CEM, CEM+, Congo, CongoJr, cRRFU, DAS, Dimmer, Distribution, DMX, ECMUX, Element, ELTS, Emphasis, Eos, ETCLink, Ethernet, Express, Expression, GCE, Idea, Ion, Irideon, K96, KnowledgeBase, Legacy Unison, LMI, Lon, MDD, MDR, MicroII, MicroVision, MIDI, MPE, NCE, Net2, Net3, Obsession, ObsessionII, Pharos, RDM, Response, RFR, RFU, RRFU, RS-232, RVI, Sensor, Sensor+, SineWave, SmartBar, SmartFade, SmartFadeML, SmartModule, SMPTE, Source Four, Source4, Touchscreen, Unison, Vision, WRFU
Net 3 Four & Two Port DMX/RDM Gateway Product Page Gateway Configuration Editor (GCE) ETCNet2 Network Configuration Editor (NCE) DMX RDM Ethernet Knowledge Base: ETC Network IP Addresses RDM Discovery Interval Timing in Net3 Gateways Maximum Number of RDM Devices on a Net3 Gateway Maximum Number...
The maximum number of RDM enabled opto-splitters that may be daisy chained together is 4. Since RDM splitters have to shorten the time between some of the packets, chaining more opto-splitters will result in unsatisfactory performance. It's also important to remember that legacy DMX opto-isolators...
The maximum number of RDM devices that can be attached to a single RDM enabled port on a Net3 Gateway is 32. This matches the DMX standard for the maximum number of devices on a DMX line. However, adding an RDM opto-isolator does not increase this number.